Office for Google @ FIFC, BKC
Client: Google India.
Carpet Area: 82,594 sq.ft.
Architect: RSP Design, India
PMC: JLL India.
Consists of Basement + Ground + Sixth floor + Seventh floor.
Basement Floor Food Storage.
Ground Floor Live Kitchen.
Sixth Floor Office Area, Work Station & Micro Kitchen.
Seventh Floor Office Area & Work Station.
Ventilation design for the open kitchen. The location of Exhaust & Fresh air fan is at Terrace Floor; with a shaft length of 25 meters with many bends. Acute calculations lead to an efficiently working system.
False flooring enables flexibility & use of advancement to achieve modularity of use. We used our clash aversion design approach to limit raising of floor to 100mm only [including floor tile & crossing] for a deep floor plate. A bustrack power system enhances modularity.
Power over Ethernet [PoE] lights are used [ https://www.youtube.com/watch?v=uO6fHgeHXK0&t=1s ]
Data Centre-like server room arrangement with related systems including, Precision Air-conditong [PAC], NOVAC fire suppression system, VESDA smoke detection, rodent repellent and water leak detection.
Summary of technical details:
Electrical [for all floor] :
Maximum Demand Load: 364 kW
UPS Configuration: 125 kVA
MDF/ MMR Room 50 kVA
Mechanical [for all floor] :
Total Load: 143.9 TR
VRV System: 72 Hp
AHU Configuration: 5500/ 3700 CFM
PAC Units: 7 TR/ 3967 CFM
Water Cooled Package Units: 5.5 TR/ 2200 CFM
Kitchen Exhaust Fans: 10000/ 4450 CFM
Kitchen Fresh Air Fans: 9200/ 3200 CFM
Dry Scrubber: 10000/ 4450 CFM
Air Cooled Ducted: 5.5 TR/ 2200 CFM
Fire Fighting System:
Modular type extinguishers UPS room, Battery room, & electrical room.
ABC type extinguishers Common passages lobbies.
K type extinguishers Kitchen
CO2 ABC tye extinguishers Workstation areas.
Upright type Sprinkler Phone, Conference, Meeting, Huddle Rooms etc.
Pendent type Sprinkler Micro Kitchen